Location for the connection box
A = Specified minimum safety clearance
- Recommended location for the connection box
- Silumin box recommended in this area.
- This area should be avoided. Always use a silumin box.
In other areas, use a heat-resisting box (T 125 °C) and heat-resisting cables (T 170 °C). The connection box must be clear of obstacles. When installing the connection box to zones 2 or 3, refer to the instructions and regulations of the local energy supplier.